|Place of Origin:||CHINA|
Payment & Shipping Terms:
|Minimum Order Quantity:||1 set|
|Price:||USD 12000-18000 / set|
|Packaging Details:||wooden case|
|Delivery Time:||40-45 work days|
|Payment Terms:||L/C, T/T, Western Union|
|Supply Ability:||100 set / month|
|Concentration Of NaClO:||0.5 - 0.7 %||Capacity:||200g/h|
|NaClO Production:||40L/h||Additive:||Food Grade Salt|
|Brine Conecntration:||2.5~3%||Salt Consumption:||3.5kg Per Kg CL2|
|Power Consumption:||4kw Per Kg Cl2||Control Mode:||Full Automatic|
|Cleaning Mode:||Polarity Reverse||LCD Touch Screen:||Siemens|
200g/h Sodium Hypochlorite Generator,
Sodium Hypochlorite Generator Swimming Pool Disinfection
Swimming pool disinfection Sodium Hypochlorite Generator
Sodium hypochlorite generator summary
The Geemblue sodium hypochlorite generator is a fully automated, pre-packaged on-site hypochlorite system designed for fast and economical installation, safe operation and easy maintenance. Skids are shipped completely piped, wired and tested.
The Geemblue sodium hypochlorite generator generates a 0.8 % sodium hypochlorite solution through the electrolysis of brine, consuming only water, salt and electricity. By producing hypochlorite on-site and on-demand, the system eliminates concerns associated with transportation and storage of liquefied chlorine gas or commercial sodium hypochlorite solutions, making it ideal for any application requiring chlorination.
By producing hypochlorite on-site and on-demand, the system eliminates concerns associated with transportation and storage of chlorine gas or commercial sodium hypochlorite solutions, making it ideal for any application requiring chlorination. Due to its low concentration, the hypochlorite solution generated by the Geenblue system minimizes degradation issues of commercial hypochlorite. In addition, the system offers lower operating costs than commercial hypochlorite, typically resulting in attractive payback periods.
Principle of sodium hypochlorite generator
Salt solution contains the several kinds of ions such as Na +, H -, when electrolysis, under a certain voltage, as a result of the movement of ions in the electrolyte solution and electrode reaction, the conductive effect occurs, then CL -, OH - such as negative ion to the anode, and positive ions such as Na +, H + to the cathode, and the corresponding electrode discharge occurs, thus carries on the REDOX reaction, the corresponding material production. The electrode reaction and solution reactions is
anode: 2Cl- - 2e → Cl2；
cathode: 2H+ + 2e → H2；
2NaOH + Cl2 → NaCl + NaClO + H2O
Overall reaction as follow:
Na Cl + H2O + DC →NaClO + H2↑
♪ Potable water treatment for drinking purpose
♪ Cooling water treatment algae control
♪ Waste water treatment
♪ Effluent control including treatment of sewage.
♪ Swimming pool chlorination.
♪ Open well water treatment
♪ Hospital disinfection and hygiene maintenance
♪ Hospital waste management.
♪ Sterilizer for food processing in Hotel and Restaurants.
♪ Meat and Poultry processing facilities disinfection.
♪ Sterilizer for food consumable and perishable Packing Plants.
♪ Public places disinfection
♪ Public health water treatment to control micro-organisms, destroy hydrogen sulphide (rotten egg odour), colour algae growth and keeps transmission pipes clean.
♪ Laundry and bleaching.
♪ General purpose domestic bleach and disinfectant.
♪ Poultry water disinfection.
♪ General farm sanitation, odour control.
♪ Dairy equipment sterilization
♪ Manufacture of oxidized starch.
♪ Bleaching of textiles, paper shellac, carpets, alginates.
|Model||chlorine capacity||Water treatment capacity||concentration||flow rate||salt conversion||energy conversion|
|GBI-50-NACLO||50 g / h||1000 ton / day||5000~7000 ppm||10 L / h||3.5 kg / kg Cl2||4 kwh / kg Cl2|
|GBI-100-NACLO||100 g / h||2000 ton / day||5000~7000 ppm||20 L / h||3.5 kg / kg Cl2||4 kwh / kg Cl2|
|GBI-200-NACLO||200 g / h||4000 ton / day||5000~7000 ppm||40 L / h||3.5 kg / kg Cl2||4 kwh / kg Cl2|
|GBI-300-NACLO||300 g / h||6000 ton / day||5000~7000 ppm||60 L / h||3.5 kg / kg Cl2||4 kwh / kg Cl2|
|GBI-400-NACLO||400 g / h||8000 ton / day||5000~7000 ppm||80 L / h||3.5 kg / kg Cl2||4 kwh / kg Cl2|