Payment & Shipping Terms:
|Capacity:||50 Kg / H Active Chlorine Production||Raw Material:||Water And Salt|
|Dimensions:||2000*800*1600 Mm||Flow:||6250 L / H|
|Power Consumption:||4 Kwh/kg Cl2||Concentration:||0.7-0.9 % (7000-9000ppm)|
|Electrolytic Liquid:||2.5% - 3% Weak Brine||Salt Consumption:||3kg (per Kg Active Chlorine)|
sodium hypochlorite equipment,
sea water generator
4 kwh / kg Cl2 Industrial Water Treatment Equipment Naclo Machine
Electrochlorination is a simple and proven technology to convert ordinary salt water [or brine or seawater] into Sodium Hypochlorite by means of Electrolysis. It is produced and applied on site. The device which uses this technology is named as Electrochlorinator or Onsite Hypo Generator.
Sodium Hypochlorite is universally accepted for combating slime, algae and other Bio-organisms in Water. The most important aspect of Sodium Hypochlorite usage is its economy effectiveness in killing bio organisms thereby disinfecting water. Electrochlorinators find application where Chlorine is not readily available or where operation with chlorine is not acceptable. Electrochlorinators therefore, find application in Drinking Water Treatment, Cooling Water Treatment, Waste Water Treatment, Bleaching, Pharmaceutical formulations and other industrial applications.
Principle of sodium hypochlorite generator
Salt solution contains the several kinds of ions such as Na +, H -, when electrolysis, under a certain voltage, as a result of the movement of ions in the electrolyte solution and electrode reaction, the conductive effect occurs, then CL -, OH - such as negative ion to the anode, and positive ions such as Na +, H + to the cathode, and the corresponding electrode discharge occurs, thus carries on the REDOX reaction, the corresponding material production. The electrode reaction and solution reactions is
anode: 2Cl- - 2e → Cl2；
cathode: 2H+ + 2e → H2；
2NaOH + Cl2 → NaCl + NaClO + H2O
Overall reaction as follow:
Na Cl + H2O + DC →NaClO + H2↑
Why choose onsite sodium hypochlorite generator
Safe Raw Material: only salt and water required;
Safe Production: the concentration of NaClO less than 1% which is classified as a non-hazardous chemical.
2. Low running cost
To produce 1 kg available chlorine, only cost 3.5 kg of salt, 4 kwh of energy.
3. Onsite generation and dosing
No chemical transportation and storage, it can be run and stop in any time.
4. Easy Operation
Full computer program and central control by PLC, the staff can operate after simple training.
|Model||FAC capacity||Water treatment capacity||Salt consumption||Power consumption||FAC concentration||Dimensions|
|GBS-15K-NACLO||15 kg / h||300000 ton / day||3.5 kg / kg Cl2||4 kwh / kg Cl2||7000~9000 ppm||2000*800*1600 mm|
|GBS-17K-NACLO||17 kg / h||340000 ton / day||3.5 kg / kg Cl2||4 kwh / kg Cl2||7000~9000 ppm||2000*800*1600 mm|
|GBS-20K-NACLO||20 kg / h||400000 ton / day||3.5 kg / kg Cl2||4 kwh / kg Cl2||7000~9000 ppm||2000*800*1600 mm|
|GBS-25K-NACLO||25 kg / h||500000 ton / day||3.5 kg / kg Cl2||4 kwh / kg Cl2||7000~9000 ppm||2000*800*1600 mm|
|GBS-30K-NACLO||30 kg / h||600000 ton / day||3.5 kg / kg Cl2||4 kwh / kg Cl2||7000~9000 ppm||2000*800*1600 mm|
|GBS-40K-NACLO||40 kg / h||800000 ton / day||3.5 kg / kg Cl2||4 kwh / kg Cl2||7000~9000 ppm||2000*800*1600 mm|
|GBS-50K-NACLO||50 kg / h||1000000 ton / day||3.5 kg / kg Cl2||4 kwh / kg Cl2||7000~9000 ppm||2000*800*1600 mm|
Contact Person: wu