|Place of Origin:||China|
Payment & Shipping Terms:
|Minimum Order Quantity:||1 set|
|Price:||USD 46000 ~ 50000 / set|
|Packaging Details:||wooden case|
|Delivery Time:||40-45 works days|
|Payment Terms:||L/C, T/T, Western Union|
|Supply Ability:||30 set / month|
|Output:||2 KG/H||Inlet Water Pressure:||0.2-0.4Mpa|
|Inlet Water Temperature:||5-27℃||Content Available CL:||7000 – 9000 Mg / L|
|Electrolyte Flow:||250 L / H||Thickness Of Electrodes:||2mm|
|Water Treatment Capacity:||40000 M3/day||Rated Current:||Determined According To The Selected Product Model|
sodium hypochlorite equipment,
sea water generator
0.2 – 0.4Mpa Inlet Water Pressure Sodium Hypochlorite Generators 2 KG/H
Guangzhou Geemblue Environmental Equipment Co., Ltd. is a high-tech enterprise which devoting energy into the development and application of the most advanced water treatment technology. It holds 4 patents of inventions, 15 utility model patents, Appearance patent and a total of 21 software copyrights, besides that, Geemblue is also undertaking 15 research projects of Guangzhou local Government.
The company has been focusing on serving municipal utility plants, sewage treatment plants, power plants, oil platforms, mariculture and food processing plants, etc. and providing quality water treatment equipment and water treatment solutions, so far, the company has been a business partner of many large environmental companies at home and abroad.
The sodium chloride contained in seawater or brine flow between sets of electrodes (anodes and cathodes) in an electrolyzer.
The chemical reactions which take place in the electrolyzer between chlorine and Sodium hydroxide produced by electrolysis.
In the electrolyzer the sodium chloride is completely dissociated into the ions Na+ and Cl-, causes the following electrochemical and chemical reactions:
at the anode: 2Cl- - 2e → Cl2；
at the cathode: 2H+ + 2e → H2；
2NaOH + Cl2 → NaCl + NaClO + H2O
Overall reaction as follow:
NaCl + H2O + DC →NaClO + H2↑
The process of the sodium hypochlorite generator
The operation of the Geemblue system is simple:
1. Salt Dissolving
Influent water passes through a water softener to reduce hardness therefore reducing the scaling of electrodes. Using softened water to dissolve the salt in a tank to form a concentrated brine solution.
2. Brine Proportioning
The saturated brine will be diluted into 2.5%-3%, the diluted brine can be adjusted and real-time monitored according to the value conductivity meter
3. Brine electrolysis
The diluted brine solution is passed through an electrolytic cell that, using DC current from a rectifier, electrolyzes the diluted brine into a 0.8% solution of sodium hypochlorite
4. Sodium hypochlorite solution storage
The final product 5000-7000 ppm (adjustable) of sodium hypochlorite solution will be kept in the storage tank and the hydrogen will be blown out to the air
The sodium hypochlorite solution will be delivered into the water by dosing pump and the dosing rate of dosing pump can be adjusted by the feedback data of residual chlorine meter and PLC
Compared with other disinfection methods
|On-site prepared NaClO||The safest chemical disinfection method, environmental non-toxic, liquid dosing, on site and on demand|
|Liquid chlorine||Chlorine is toxic and corrosive. Chlorine transport and storage are unsafe, easily cause leaks and explosions, harm to human life and the environment|
|Commercial NaClO||Dangerous goods, unsafe to transport and storage, When stored easily degradable and the storage time is short. High transport costs, the liquid dosing|
|Chlorine Dioxide||Compound type reaction was not complete, dosing by-product exceeded; high purity type operating costs, are not suitable for medium-sized water plant|